Deposits build up very quickly at the bottom of industrial steam boilers.
The way to remove these deposits effectively is by very rapidly opening and closing a valve at the bottom of the boiler, this is called intermittent blowdown.
It is an extremely demanding application which requires a robust and reliable product.
The GESTRA bottom blowdown valve achieves this by opening very quickly, for just 2 seconds, producing a vacuum at the bottom of the boiler.
The resulting suction removes settled sediment, known as sludge, from the bottom of the boiler.
When the valve closes its design ensures tight shut-off with no leakage.
Opening the valve for longer than 2 seconds has no further effect at reducing blowdown and simply wastes water.
|A1130 - MPA46 and 47 Actuation Kit||English||DBL_A1130||Download PDF|
|Blowdown Timer PRS 50||English||DBL_850651||Download PDF|
|Intermittent Blowdown Valves Type PB24C (Key Handle) and MPB24C (Actuated)||English||DBL_FCD GSEDS0043||Download PDF|
|Programme-controlled blowdown system TA 10||English||DBL_850874||Download PDF|
|Programme-Controlled Blowdown System TA 5, TA 6||English||DBL_818559||Download PDF|
|Programme-controlled blowdown system TA 50||English||DBL_850875||Download PDF|
|Programme-Controlled Blowdown System TA 7||English||DBL_818557||Download PDF|
|Rapid-Action Intermittent Blowdown Valve PA 110, MPA 110 PN 160/250, CL 600/900/1500 DN 25||English||DBL_810445||Download PDF|
|Rapid-Action Intermittent Blowdown Valve PA 46, PN 40 / CLASS 150 / 300, DN 20-50 PA 47, PN 63 / CLASS 600, DN 25, 40, 50 PA 48, PN 100 / CLASS 600, DN 25, 40, 50 MPA 46, PN 40 / CLASS 150 / 300, DN 20-50 MPA 47, PN 63 / CLASS 600, DN 25, 40, 50 MPA 48, PN 100 / CLASS 600, DN 25, 40, 50||English||DBL_818424||Download PDF|
|Control technique installation instructions - programme-controlled blowdown systems TA 5, TA 6, TA 4 (de-en)||International||BAN_808399||Download PDF|
|Original installation instructions - programme-controlled blowdown system TA 7 (de-en-fr-es-it)||International||BAN_808403||Download PDF|
|Installation Instructions Programme-Controlled Blowdown System TA 10||International||BAN_809178||Download PDF|
|Installation Instructions Programme-Controlled Blowdown System (EN_DE)||International||BAN_809180||Download PDF|
|Rapid-action intermittent blowdown valve PA 46, PA 47, PA 48, MPA 46, MPA 47, MPA 48||English||BAN_818447||Download PDF|
|Rapid-action intermittent blowdown valve PA 110, MPA 110||English||BAN_819045||Download PDF|
EU Declaration of conformity